Bowne (NYSE: BNE) provides financial, marketing and business communications services around the world. In an effort to improve the energy efficiency of its HVAC systems, Bowne engaged Dalkia to provide restoration services for the rooftop units (RTUs) at its facility.
Dalkia technicians performed analysis of the RTUs, identifying several sources of energy inefficiencies. The team implemented mechanical, thermal and air flow adjustments as well as the overall reconditioning of the system components. Through this process the overall system efficiency was boosted from 22% to 92%, which reduced energy consumption by $21,884 per year.
|Technical Results||Before Restoration||After Restoration||Improvement|
|Tons of A/C||20||20|
|CFM Air Flow||1,959||6,444||229%|
|Evaporator Coil Air Temp||73.2F||65.6F||12%|
|Overall Unit Efficiency||22%||95%|
|Annual Operating Hours||432|
|Annual Operating Cost Before Restoration||$37,906|
|Annual Operating Cost After Restoration||$16,076|
|Annual Operating Cost Savings||$21,884|
|Return on Investment||114%|